Wine Cellar Refrigeration Service Call M&M Los Angeles – Refrigerant Leak Intro – Part Three
We’re now back to where we got the unit and
put it back together. I’ve got the unit closed up again and I was able to find the leak at
the bottom of the unit there mostly. It’s not something I can physically fix like I
was thinking, only because there are porous leaks. So it’s almost like refrigerant seeping
through. It is common with wine refrigeration equipment, because of the amount of humidity
that the equipment works with. So what we’re going to do next to proceed and fix and remedy
the problem is we’re going to add an additive to the system. When adding those additives,
it seals very small leaks normally found in the evaporator coils. If it was a weld or
something that came off, then I would be welding it right now. But it’s not. So the way to
address is to add a stopper. So the leak isn’t in one of the tubes that
go into it? The pipes that go into it? The leak is actually where?
It’s actually all around the copper. So it’s not in a specific point. It’s multiple locations.
Right. Unfortunately, I cannot take heat directly
on to that area because of the fence are made of aluminum and copper
But the copper where you’re saying the leak is, what part of the system is it?
This is the evaporator coil. So it’s actually in the coil. Is that where
the leak is? Correct. So it’s not in a component or an
exterior part of the coil or outside the coil. It’s actually within the coil area. The coil
area consists of fence and two going out from side to side. And fence, aluminum fence, that
go up and down, which is where the heat transfer happens. This is where all the heat get absorbed
and transferred, carried over by the refrigerant. So to fix it, where going to…
So to fix it, what I’m going to have to do is I’m going to have to add a stop leak. It’s
a dye. It’s a substance. It comes in a can usually. You got to be careful when adding
those type of substances to the equipment because you have to make sure that it’s set
up for the right tonnage. In other words, the capacity of the equipment. You don’t want
to put it in a bottle like that’s due a large system, because you can clog up the equipment.
You can have a failure. So it’s important just to get the right balance
so that… It’s important to get the right can.
And how are you going to add it? Are you going to add it to the…
That is added in the condensing unit… Which is outside…
Which is outside. So we’re going to go back up there. We’re going to be adding the Freon
first. The stop leak’s going to be the last thing we add to the system before we put the
system back online and get it running. And what is the likelihood is that that will
fix the problem? For something like this about 50%…
About 50% chance that… Chance that it’ll repair the leak.
And if it doesn’t? And if it doesn’t, then we will find out in
a month when we do the follow up based on the Freon level if it’s leaked or not. So
until then we won’t really know but in comparison to replacing the equipment, this gives you
the opportunity to save a lot more by using the remedy.
So this is basically, try the stop leak, and if that fixes it, great. If it doesn’t, then
the unit will actually have to be… If it fixes, then you can get another 5 or
10 years depending… I have had good… would say that in most cases when I’ve used it,
9% of the times that I’ve used it I haven’t had any problems.
But if it doesn’t work? But if doesn’t work, then we’re back to the
original problem, which at the point we’ll have to replace the evaporator coil.
Alright, cool! So you’re saving the clients some money, hopefully!
Hopefully we can save the customer some money here and get away from trying to replace the
unit right now.